By Ruth Jordan on January 26 2018 13:50:36
US single-phase residential power distribution transformer, showing the two insulated "Line" conductors and the bare "Neutral" conductor (derived from the earthed center-tap of the transformer). The distribution supporting cantenaries are also shown.
Architectural wiring diagrams show the approximate locations and interconnections of receptacles, lighting, and permanent electrical services in a building. Interconnecting wire routes may be shown approximately, where particular receptacles or fixtures must be on a common circuit.
The wiring diagram lets you define the different installation components and locations (cabinets, control panels, consoles, connection boxes, etc.) and gives you a synoptic, functional view of the installation. The terminal strips and cabling connections between locations can be defined at the beginning, during or at the end of the project design. The length of the pathways can also be defined by the user and thus serve as a default value, for all cables within the given pathway.
Cables usually are secured with special fittings where they enter electrical apparatus; this may be a simple screw clamp for jacketed cables in a dry location, or a polymer-gasketed cable connector that mechanically engages the armour of an armoured cable and provides a water-resistant connection. Special cable fittings may be applied to prevent explosive gases from flowing in the interior of jacketed cables, where the cable passes through areas where flammable gases are present. To prevent loosening of the connections of individual conductors of a cable, cables must be supported near their entrance to devices and at regular intervals along their runs. In tall buildings, special designs are required to support the conductors of vertical runs of cable. Generally, only one cable per fitting is permitted, unless the fitting is rated or listed for multiple cables.