In North American practice, an overhead cable from a transformer on a power pole to a residential electrical service usually consists of three twisted (triplexed) conductors, with one being a bare neutral conductor, with the other two being the insulated conductors for both of the two 180 degree out of phase 120 V line voltages normally supplied. The neutral conductor is often a supporting "messenger" steel wire, which is used to support the insulated Line conductors.
Each type of switch has a different symbol and so do the various outlets. There are symbols that show the location of smoke detectors, the doorbell chime, and thermostat. On large projects symbols may be numbered to show, for example, the panel board and circuit to which the device connects, and also to identify which of several types of fixture are to be installed at that location.
Cables usually are secured with special fittings where they enter electrical apparatus; this may be a simple screw clamp for jacketed cables in a dry location, or a polymer-gasketed cable connector that mechanically engages the armour of an armoured cable and provides a water-resistant connection. Special cable fittings may be applied to prevent explosive gases from flowing in the interior of jacketed cables, where the cable passes through areas where flammable gases are present. To prevent loosening of the connections of individual conductors of a cable, cables must be supported near their entrance to devices and at regular intervals along their runs. In tall buildings, special designs are required to support the conductors of vertical runs of cable. Generally, only one cable per fitting is permitted, unless the fitting is rated or listed for multiple cables.
Associated circuit protection, control and distribution devices within a building wiring system are subject to voltage, current and functional specification. Wiring safety codes vary by locality, country or region. The International Electrotechnical Commission (IEC) is attempting to harmonise wiring standards amongst member countries, but significant variations in design and installation requirements still exist.
trailer wiring diagram
wiring diagram samples
Loop at switch lighting circuits lighting loop at switch newcolours electric light wiring diagram
Charming wiring diagram pin plug chevy colorado tested goodive replaced the resistor 808x1059 electric light uk
Diagram electric light wiring uk ceiling fan wall switch to and home for
Three way light switching circuitagram old cable colours electric wiring uk