By Jennifer Mireles on January 16 2018 14:21:02
Cables usually are secured with special fittings where they enter electrical apparatus; this may be a simple screw clamp for jacketed cables in a dry location, or a polymer-gasketed cable connector that mechanically engages the armour of an armoured cable and provides a water-resistant connection. Special cable fittings may be applied to prevent explosive gases from flowing in the interior of jacketed cables, where the cable passes through areas where flammable gases are present. To prevent loosening of the connections of individual conductors of a cable, cables must be supported near their entrance to devices and at regular intervals along their runs. In tall buildings, special designs are required to support the conductors of vertical runs of cable. Generally, only one cable per fitting is permitted, unless the fitting is rated or listed for multiple cables.
A wiring diagram usually gives information about the relative position and arrangement of devices and terminals on the devices, to help in building or servicing the device. This is unlike a schematic diagram, where the arrangement of the components, interconnections on the diagram usually does not correspond to the components, physical locations in the finished device. A pictorial diagram would show more detail of the physical appearance, whereas a wiring diagram uses a more symbolic notation to emphasize interconnections over physical appearance.
A schematic shows the plan and function for an electrical circuit, but is not concerned with the physical layout of the wires. Wiring diagrams show how the wires are connected and where they should located in the actual device, as well as the physical connections between all the components.
The wiring diagram lets you define the different installation components and locations (cabinets, control panels, consoles, connection boxes, etc.) and gives you a synoptic, functional view of the installation. The terminal strips and cabling connections between locations can be defined at the beginning, during or at the end of the project design. The length of the pathways can also be defined by the user and thus serve as a default value, for all cables within the given pathway.